Will Low-Flow Toilets Work In An Older Home?
Installing low-flow toilets is a great way to conserve water and reduce your water bill. By using about half the volume of water as a standard toilet, you can save around a gallon and a half of water per flush. That adds up to thousands of gallons of water saved every year.
Many states and municipalities now require low-flow toilets on new homes or when replacing a toilet when remodeling a bathroom. For most homeowners, the process is simple and straightforward, but what if your home is 50 years old or older? Can your plumbing system handle a lower flow toilet?
The key to whether a low-flow toilet will function in an older home is the waste drain pipe slope. The waste pipe beneath a toilet needs a slope of between 1/8-in. and 1/4-in. per foot for the water to carry solid waste to the sewer. If it’s too steep or not steep enough, the flow of water could allow waste to collect, causing a clog.
In some older homes the slope may not have been carefully planned. Since older toilets had plenty of flushing power with 3 gallons of water to work with, it may not have been a concern.
If you have an older house, here are some things to be aware of if you decide to install low-flow toilets.
1. If your current toilet backs up occasionally, even when solid waste isn’t being flushed you may have a clogged waste line. Have the waste and sewer line inspected prior to installing a low-flow toilet.
2. When the toilet is lifted off the floor for other maintenance, use a flashlight to check the drain for standing water in the waste line. Even if it’s just a small amount, it could be a sign that you have a negative pipe slope.
If you’re concerned that your older plumbing system may not be able to safely handle a low-flow toilet, consider installing a unit with a pressure-assisted flush that uses water pressure to charge a compressed-air tank inside the toilet tank. When flushed, it will use the compressed air to drive water out of the bowel fast, forcing it down the drain and into the waste line with enough force to remove solid waste.
Have questions about low-flow toilets? Call ABC Plumbing, Sewer, Heating, Cooling and Electric. We can help answer all your plumbing questions.
Neighbors Are Saying About ABC
“Tom was awesome! He is very personable and explains the whole process well. He did a great job and ensured that he used 5-star service throughout the process. I will definitely use ABC and Tom again in the future for electrical work.”–
“Bill showed up on time to repair our broken air conditioner. ABC kept in touch throughout the day to let me know time he would be arriving too. Bill was professional, friendly, helpful, and knowledgeable. We wound up signing up for monthly care package because Bill and ABC really made…”–
“We were very pleased with the service performed by Brett Pack in performing the annual maintenance of our air conditioning unit. He noted it was low on refrigerant, which he then added after consulting with us. He also made sure we took advantage of all available discounts.”–
“Tom did a super job fixing our electrical problem. He is one of the best electricians I have ever had in my home for repair work. I would highly recommend Tom and ABC Company if you need any type of electrical work. He took his time and explained everything and…”–
“I am so impressed with Chris and ABC Plumbing, Sewer, Heating, Cooling and Electric. His friendliness honest approach to his Job is remarkable. Thanks Chris for making my day and believing that they are still great honorable people out there.”–
“Our AC was not working in the 90-degree summer heat. Josh identified that power was not going to the furnace blower. He identified that power was not going to the furnace breaker. His keen eye spotted that the wire leading into the breaker had frayed. He cut out the frayed…”–